This section contains information on site planning and requirements for installing the
Site Environmental Requirements
The following table lists the environmental requirements for the
Server Access Clearance
A minimum clearance of 36 inches in front of and behind the chassis for maintenance access as well as air flow.
41°F to 104°F (5°C to 40°C) up to 6,000 feet (1,829 meters)
-40°F to 158°F (-40°C to 70°C)
-197 feet to 6,000 feet (-60 to 1,800 meters) at 104°F (40°C).
Width: 17.16 inch excluding mounting ears
0.1G, 5-100Hz, 0.1 Oct/min
Site Power Requirements
The following table lists the
Operational DC Voltage (Nominal)
Operational DC voltage (Minimal)
Operational DC voltage (Maximum)
DC Input Treatment
Isolated DC Return
Maximum DC Current
Operational AC Voltage (Nominal)
100-120 VAC @ 50-60 Hz
Maximum AC Current
12 A / 7 A
An AC power cord is included in SBC shipments for SBCs equipped with AC power supplies.
(North American 15 A 125 VOLT NEMA 5-15P to IEC C19 Connector)
|Bonding||Bonded to a grounding system utilizing either an Isolated Bonding Network |
(Isolated Ground) or a Common Bonding Network (Integrated Ground).